James Stallcup Sr. & Jr.
A new 110.15 has been added that explains the use and location of the high-leg from the service equipment, feeder circuits, branch-circuits and other electrical related equipment throughout the NEC.
Author’s Note: The marking of the high-leg should be in Article 110 where it would apply to all types of installations and not just to services, feeders and switchboards and panel boards. The new 110.15 will meet the intent of the NEC and also simplify the application of the rules pertaining to the high-leg. Also review 210.4(D), 215.8, 230.56, and 408.3(E), FPN.
|Type of Change
||Accept in Part
|pg. 73||# 1-233||pg. 41||# 1-136
|log 1499||CMP 1
||log 1135||Submitter Larry Wendt - Mark Berner||1999 NEC 110-15||IEC -||